The Context Plus XP95 Manual Call Point is intended for indoor applications and incorporates a short circuit isolator which will ensure its operation in the event of a short circuit fault on the loop.
The Call Point is surface mountable and has an easily resettable element rather than a break glass. It also features a unique ‘Plug and Play’ installation concept designed specifically to reduce installation time. The call point utilises a terminal block, where all installation cabling is terminated.
Its address is set at the commissioning stage by means of a seven-segment DIL switch. A single bi-coloured alarm LED is provided which is controlled independently of the call point by the control panel. The LED is illuminated red when the call point has been activated and amber/yellow to indicate a short circuit.
Once activated, the Call Point can be reset by inserting the test key into the bottom of the unit until the key clicks into position, next remove the test key and push the front cover up until it clicks home.
Feel free to ask any questions over the phone, or get in touch via our contact form below. Your message will be dispatched directly to our staff who will answer as soon as they can.